Panasonic Electric Works Fire & Security Technology Europe AB
Citadellsvägen 23, SE-211 18 Malmö, Sweden
Tel: +46 (0)40 697 70 00 • Fax : +46 (0)40 697 70 99
firstname.lastname@example.org • www.panasonic-fire-security.com
Fire alarm systems
External Fire Brigade
• Control (key required) and indicating panel for the fire brigade personnel, etc.
• Compact size
Ext. Fire Brigade Panel
This unit (S/W V1.2) is primarily intended
to be used by the fire brigade personnel, i.e.
for pre-warning, co-incidence, fire and
heavy smoke / heat alarm presentation.
Point or zone alarm presentation and fire
alarm reset are as in the c.i.e. it is connected
to. You can scroll amongst two or more
alarms in the system. All or selected alar ms
will be presented in a display (LCD, 2x40
characters with back-light). An alarm text
will be presented together with each alarm,
if programmed in the c.i.e. Furthermore,
>617 texts for selected alarms can be stored
in the unit and will in such a case be shown,
instead of the texts sent from the c.i.e. for
these alarms. A built-in buzzer will sound
like in the c.i.e. Any fault in the system will
be presented as "General fault in system"
and the buzzer will sound. The unit is
power supplied via the c.i.e. or ext. power
LEDs, push buttons etc.
The unit has the following LEDs:
• Fire and Alarms queued, indicating
pre-warning, co-incidence, fire and
heavy smoke / heat alarm
• Operation, indicating that the unit is
connected to a c.i.e. and power
supplied, i.e. it is in operation.
• Extinguishing, indicating activated
output for Extinguishing equipment.
• Ventilation, indicating activated output
for Ventilation equipment.
• Fire brigade tx, indicating activated
output for Fire brigade tx (routing
The unit has the following push buttons:
• Alarms queued, used to scroll amongst
• Silence buzzer, used to silence the
buzzer (it will re-sound for a new
• Silence alarm devices, used to silence
the alarm devices (they will re-sound
for a new alarm.
• Reset, used to reset the fire alarms.
The designation texts on the front are in
1828SE in Swedish but a neutral front for
other languages is available (1828CC).
The compact size enclosure is made of grey
high impact ABS. Fitted with a supple-
mentary "O" ring gasket, it will comply with
IP61, in respect of dust and moisture. A key
is required to get access to the push buttons
and they are disabled until they are supposed
to be used. A key is not required for the
alarm presentation and to silence the buzzer.
Two compression glands are attached. The
unit shall be wall mounted.
SW mode and address setting
The display and the push buttons are used to
set the SW mode and address, see the
opposite side of this page.
The 1828 unit is intended for indoor use and
in dry premises. SW mode 1826/28 - 1587
is intended to be used in the systems
EBL512 and EBL128 SW mode 1826/28 –
1582 in the systems EBL500 / 512 / 1000 /