Panasonic Electric Works Fire & Security Technology Europe AB
Citadellsvägen 23, SE-211 18 Malmö, Sweden
Tel: +46 (0)40 697 70 00 • Fax : +46 (0)40 697 70 99
firstname.lastname@example.org • www.panasonic-fire-security.com
Fire alarm systems
Alert annunciation units
1735 and 1736
• Control and indicating unit for alert annunciation
• Compact size
Alert annunciation unit
When the Alert Annunciation function shall
be used in the systems EBL512 & EBL128
an AA unit is required to present the AA
alarms and for the related manoeuvres, i.e.
to acknowledge / reset the alarms. For a
detailed description of the AA function, see
Planning and Operating instructions for the
Point or zone alarm presentation is as in the
c.i.e. it is connected to. When there are
queued alarms in the system, you can scroll
amongst them. All or selected alarms will
be presented in the unit's display (LCD,
2x40 characters with back-light). A user
definable text message will be presented
together with each alarm, if programmed in
the c.i.e. Furthermore, > 617 texts can for
selected alarms be stored in the unit and will
in that case be shown, instead of the texts
sent from the c.i.e. for these alarms. A built-
in buzzer will sound to indicate a not
acknowledged AA alarm. The unit is power
supplied via the c.i.e. or ext. power supply.
LEDs, push buttons etc.
The unit has the following LEDs:
• Fire and Alarms queued, indicating fire
alarm / AA alarm.
• Operation, indicating that the AA
function is enabled in the system.
Normally a time channel is used to
enable this function.
• Fire brigade alerted, indicating that the
"Fire brigade tx" output is activated in
the c.i.e. because:
- the activated alarm is not an AA alarm
- the AA function has been ended, e.g.
the acknowledge or investigation time
has run out, etc.
• Acknowledge, indicating that the AA
alarm has been acknowledged.
The unit has the following push buttons:
• Alarms queued, used to scroll amongst
• Acknowledge, used to acknowledge an
AA alarm and hereby also silence the
• Reset, used to reset an AA alarm.
1735 has the designation texts in Swedish.
1736 has a neutral front for other languages,
see the opposite side of this page. (This
front also holds one extra LED & two extra
The compact size enclosure is made of grey
high impact ABS. Fitted with a supple-
mentary "O" ring gasket, it will comply with
IP61, in respect of dust and moisture. The
unit has no door, i.e. the front is accessed
directly, when required. The push buttons
are disabled until they are supposed to be
used. The unit shall be wall mounted. Two
compression glands are attached.
SW mode and address setting
The display and the push buttons are used to
set the SW mode and address.
The SW modes are described on the
opposite side of this page.
The units are intended for indoor use and in
dry premises. They are intended to be used
in the systems EBL512 & EBL128. An
External FBP / DU interface board 1587 is
required in the EBL512 c.i.e. and a 4552
Transceiver component in the EBL128 c.i.e.