Panasonic Electric Works Fire & Security Technology Europe AB
Citadellsvägen 23, SE-211 18 Malmö, Sweden
Tel: +46 (0)40 697 70 00 • Fax : +46 (0)40 697 70 99
email@example.com • www.panasonic-fire-security.com
Fire alarm systems
External Fire Brigade
• Control and indicating panel for the fire brigade personnel
• Built-in printer (option)
Ext. Fire Brigade Panel
This unit is intended to be used by the fire
brigade personnel, i.e. for pre-warning, co-
incidence, fire and heavy smoke / heat alarm
presentation. Point or zone alarm
presentation and fire alarm reset are as in the
c.i.e. it is connected to. You can scroll
amongst two or more alarms in the system.
All or selected alarms will be presented in
the unit's display (LCD, 2x40 characters
with back-light). An alarm text will be
presented together with each alarm, if
programmed in the c.i.e. Furthermore, >
617 texts for selected alarms can be stored in
the unit and will in such a case be shown,
instead of the texts sent from the c.i.e. for
these alarms. A built-in buzzer will sound
like in the c.i.e. Any fault in the system will
be presented as "General fault in system"
and the buzzer will sound. The unit is
power supplied via the c.i.e. or ext. power
LEDs, push buttons etc.
The unit has the following LEDs:
• Fire and Alarms queued, indicating
pre-warning, co-incidence, fire and
heavy smoke / heat alarm.
• Operation, indicating that the unit is
connected to a c.i.e. and power
supplied, i.e. it is in operation.
• Extinguishing, indicating activated
output for Extinguishing equipment.
• Ventilation, indicating activated output
for Ventilation equipment.
• Fire brigade tx, indicating activated
output for Fire brigade tx (routing
The unit has the following push buttons:
• Alarms queued, used to scroll amongst
• Silence buzzer, used to silence the
buzzer (it will re-sound for a new
• Silence alarm devices, used to silence
the alarm devices (they will re-sound
for a new alarm.
• Reset, used to reset the fire alarms.
• , used for paper feed, when the unit is
provided with a printer 1835 (option).
The designation texts on the front are in
1826SE in Swedish but a neutral front for
other languages is available (1826CC).
Ext. FBP 1826 & Printer 1835
The ext. FBP 1826 consists of a grey metal
cabinet with a door. A key is required to
open the door, which has a Plexiglas in front
of the FBP front, see photo. It has cable
inlets on the top, bottom and back sides and
is intended to be wall mounted. Two
compression glands are attached.
A Printer 1835 can be mounted in the ext.
FBP 1826. It will print all the alarms,
including the alarm texts.
SW mode and address setting
The display and the push buttons are used to
set the SW mode and address, see the
opposite side of this page.
The 1826 unit is intended for indoor use and
in dry premises. SW mode 1826/28 – 1587
2nd Cab is intended to be used in the
systems EBL512 and EBL128 and SW
mode 1826/28 – 1582 2nd Cab in the
systems EBL500 / 512 / 1000 / 2000.